Fully automatic self-testing emergency lighting incorporating a central monitoring facility in accordance with ATS type PER classification, as classified by BS EN 62034.
Individual luminaires incorporate self-contained emergency lighting operation with built-in standalone self-testing in accordance with ATS type S, as classified by BS EN 62034 and facility for connection to a central monitoring and control facility by an unscreened two wire communications bus operating at a nominal voltage of 28v d.c.
Loss of connection of the communications bus to a luminaire causes that luminaire to revert to standalone self-testing operation.
The condition of each luminaire is automatically recorded by the central monitoring facility and also indicated locally at the luminaire.
Failure of any luminaire during testing or the failure of the supply to the central monitoring facility is signalled via a GSM link to designated email recipients and as SMS messages to designated recipients.
A monitoring service may be designated to receive messages and provide a maintenance service.
As Fastel SRM – remote emergency lighting monitoring technology.